- Sometimes harmonic resonance occurs between power capacitor and transformer which may cause high magnification of harmonics.
- The resonance can happen at one particular frequency is called as resonance frequency ( f_{r} ) in a system in which inductive reactance ( X_{L} ) and capacitive reactance ( X_{C} ).
- The net impedance becomes low when the inductive reactance X_{L} is equal to capacitive reactance X_{C}.
- The magnitude of the current becomes high particularly at resonance frequency.
- The resistance of the network will limit the current.
- Series resonance due to external harmonics in the supply system and resonance between capacitor in the electrical system
- Parallel resonance within a given electrical system and resonance between internal capacitors and inductive loads
- Typically, the inductive reactance of the system remains constant but the capacitive reactance varies in order to main higher power factor.
- The resonance frequency falls, if the capacitor increases as the resonance frequency is inversely proportional the capacitance.
- Lower the resonance frequency is dangerous because it may match with any harmonics and causes more damage.
f_{r}
= 1 / 2π √ LC
Causes of Harmonic Resonance
- Over heating of bus bar
- Higher rate of failure of equipment
- Frequency failure of capacitors
- Frequent blow of fuses
- False tripping of MCCBs
Reduction of Harmonic Resonance
- The harmonic resonance is reduced by DETUNE FILTER which consists of reactor is in series with each capacitor.
- The detune filter creates one resonance frequency which offers higher impedance for high frequency harmonics.
- The resonance at higher frequency harmonics ( 5^{th} harmonics and above ) can be avoided.
Example
A 500 kVA industrial transformer with
percentage impedance % Z = 4.5 with 500 kVA automatic power factor correction
panel. Calculate the resonance frequency. |
Solution
Short
circuit power kVA_{sc} = kVA / ( % Z / 100 )
=
500 / ( 4.5/100 )
=
500 / 0.045
= 11,111 kVA
Resonance
frequency f_{r} = f × √ kVA_{sc} / kVAr
Where
f
= Supply frequency
f_{r}
= Resonance frequency
kVA_{sc}
= Short circuit power
kVAr
= Rating of capacitor for power factor improvement
Case
1 : 150 kVA capacitor is connected for power factor improvement
Resonance
frequency = 50 × √ 11,111 / 150
= 50 × 8.60
= 430 Hz
This frequency closely matches with the
ninth harmonic frequency ( 450 Hz ). There is no resonance occurs in this case
Case
2 : 500 kVA capacitor is connected for power factor improvement
Resonance
frequency = 50 × √ 11,111 / 500
= 50 × 4.71
= 235.5 Hz
This frequency closely matches with the
fifth harmonic frequency. The fifth harmonics is least order harmonic with
higher magnitude. The resonance at this harmonic may damage the equipment.
You may also like :
Define : Low voltage, Medium voltage
& High voltage
Substation and Transmission line of
India
Minimum clearance between transmission
line conductor and ground
Right of way ( ROW ) in the transmission line
No comments:
Post a Comment