- It consists of only single winding which is common to both primary and secondary winding.
- It has two end terminals ( PR) acts as primary and one end terminal ( either P or R ) and inter mediate terminal Q acts as a secondary winding ( Figure A ).
- The position of the intermediate terminal Q determines whether auto – transformer works as step down transformer or step up transformer.
- The theory and operation of the auto - transformer is similar to that of conventional two winding transformer.
- The auto transformer is cheaper than the ordinary transformer because of single winding uses less copper than the two winding.
- Since the voltage / turn is equal in both winding, the voltage develops across each winding depends on number of turns.

- Figure B shows a step down transformer in
which PQ winding acts as a primary having N
_{1}turns and QR winding acts as a secondary winding consists of N_{2}turns. - If the supply
voltage V
_{1}is given to primary winding

Induced emf per turn ( E

_{t}) = V_{1}/ N_{1}
As we know that the value of E

_{t}is same for both winding
Secondary voltage V

_{2}= E_{t }× N_{2}_{}

**Saving of Copper in Auto transformer as step down transformer**

- The weight of winding material ( Copper ) is proportional to the length and area of cross section of the conductors.

W a Volume of material

W a ( a × L )

- The cross section of the conductor depends on current ( I ) and length of conductors is proportional to the number of turns ( N ).
- Therefore the weight of copper is directly proportional to ampere - turns ( NI ).

Weight of the copper in the ordinary
transformer ( W

_{O}) = N_{1}I_{1}+ N_{2}I_{2}
Weight of copper in the auto transformer ( W

_{a}) =
Weight of copper in part PQ a I

_{1}( N_{1}– N_{2})
Weight of copper in part QR a ( I

_{2}– I_{1}) N_{2}
Total weight of copper in the auto
transformer a I

_{1}( N_{1}– N_{2}) + ( I_{2}– I_{1})
N

_{2}
a ( I

_{1}N_{1}+ I_{2}N_{2}– 2N_{2}I_{1})
Weight of copper in auto transformer ( W

_{a}) / Weight of copper in ordinary transformer ( W_{O}) = ( I_{1}N_{1}+ I_{2}N_{2}– 2N_{2}I_{1}) / ( I_{1}N_{1}+ I_{2}N_{2})
= ( I

_{1}N_{1}+ I_{1}N_{1}– 2N_{2}I_{1}) / 2N_{1}I_{1}( As N_{1}I_{1}= N_{2}I_{2})
= ( 2I

_{1}N_{1}/ 2I_{1}N_{1}) – ( 2N_{2}I_{1}/ 2I_{1}N_{1})
= ( 1 ) – ( K ) ( As K = N

_{2}/ N_{1}= I_{1}/ I_{2})
= 1 – K

Therefore W

_{a }= ( 1 – K ) W_{O}
Saving in Copper = W

_{O}– W_{a}
= W

_{O }– ( 1 – K ) W_{O}
= KW

_{O}

- Therefore the saving in copper material depends on the value of K ( Voltage transformation ratio ).
- Higher value of K, more saving in copper material

**Saving of Copper in Auto transformer as Step up transformer**

Weight of the copper in the ordinary transformer ( W

_{O}) = N_{1}I_{1}+ N_{2}I_{2}
Weight of copper in the auto transformer ( W

_{a}) =
Weight of copper in part PR a I

_{2}( N_{2}– N_{1})
Weight of copper in part QR a ( I

_{1 }– I_{2 }) N_{1}
Total weight of copper in the auto transformer a I

_{2}( N_{2}– N_{1}) + ( I_{1 }– I_{2 })
N

_{1}
a ( I

_{1}N_{1}+ I_{2}N_{2}– 2N_{1}I_{2})
Weight of copper in auto transformer ( W

_{a}) / Weight of copper in ordinary transformer ( W_{O}) = ( I_{1}N_{1}+ I_{2}N_{2}– 2N_{1}I_{2}) / ( I_{1}N_{1}+ I_{2}N_{2})
= ( I

_{1}N_{1}+ I_{1}N_{1}– 2N_{1}I_{2}) / 2N_{1}I_{1}( As N_{1}I_{1}= N_{2}I_{2})
= ( 2I

_{1}N_{1}/ 2I_{1}N_{1}) – ( 2N_{1}I_{2}/ 2 N_{1}I_{1})
= ( 1 ) – ( 1 / K ) ( As K = N

_{2}/ N_{1}= I_{1}/ I_{2})
= ( 1 – 1 / K )

Therefore W

_{a }= [ ( 1 – 1 / K ) ] W_{O}
Saving in copper = W

_{O}– [ ( 1 – 1 / K ) ] W_{O}
= [ 1 – 1 + 1 / K ] W

_{O}
= ( 1 / K ) W

_{O}- Therefore the saving in copper material depends on the value of 1 / K.
- Lower value of K, more saving in copper material

__Application__- The auto – transformer is used for starting of synchronous motor and induction motor. Its winding is used only during starting period of the motor for a few seconds.
- It is used as a furnace transformer for getting suitable supply voltage for furnace winding from 230 V supply.
- It is used as laboratory equipment to get suitable supply voltage as per requirement.
- To compensate the small voltage drop in a distribution cable by giving small voltage boost.
- It may be used as interconnecting transformer in 132 kV / 66 kV supply system.

__Connection of two winding transformer into Auto – transformer__- The winding connection diagram of an auto transformer from two winding transformer may be as ( I ) Step down transformer ( II ) Step up transformer

__Conversion of Two winding Transformer into Step down Auto Transformer__

__Conversion of Two winding Transformer into Step up Auto Transformer__
You may also like :

Closed focus transformers could genuinely show up positively in relationship with shell outline transformer for high voltage control transformer applications.

ReplyDeleteTransformer winding is one more standard bit of a transformer upgrade, since this is the ensured current bearing conductors contorted inside ring.Winding Machine

Really I enjoy your site with effective and useful information. It is included very nice post with a lot of our resources.thanks for share. i enjoy this post. text auto reply

ReplyDeletethank you

ReplyDeleteLeading load cos(phi) pasor plz

ReplyDeleteThis is same as transformer vector diagram

ReplyDeletehttps://myelectrical2015.blogspot.com/2017/10/transformer-on-load.html

This is such a great resource that you are providing and you give it away for free. I love seeing blog that understand the value of providing a quality resource for free. purple amethyst ring

ReplyDeleteI havent any word to appreciate this post.....Really i am impressed from this post....the person who create this post it was a great human..thanks for shared this with us. garnet engagement ring

ReplyDeleteThis is a well crafted article, if perhaps just about all bloggers provided the same worth of content while you, the web will be a far better place. Please keep it up! Amethyst Rings

ReplyDeleteReally interesting blog. I’m thankful for this valuable information. Ogen Infosystem is a leading Website Designing and Development Company in Delhi. Also, get SEO and all types of Digital Marketing Services at an affordable price.

ReplyDeleteWeb Development Company

A very delightful article that you have shared here about Electrical Enclosures. Your blog is a valuable and engaging article for us, and also I will share it with my companions who need this info. Thankful to you for sharing an article like this.

ReplyDelete