## 26/03/2021

### Dielectric Stress in Single core cable

In this theory, dielectric stress on cable, electric intensity, maximum potential gradient, minimum potential gradient, ratio of maximum to minimum potential gradient and dielectric stress on stranded cable is given.

# Dielectric Stress

• It is electrostatic stress on cable insulation under operating conditions.
• The dielectric stress at any point is equal to potential gradient at that point therefore in order to find dielectric stress at any point in cable, we have to find out potential gradient at that point.

## Electric intensity

The electric intensity at any distance x from the center of cable O is given by

Ex = [Q / 2πε0εr ] ( 1 / x )  volt / meter

Where

ε0 = Absolute Permittivity = 8.854 × 10 – 12 Farad / meter

εr = Relative Permittivity

The potential gradient ( E ) at any point is equal to electric intensity ( g ) at that point therefore

g =  [Q / 2πε0εr ] ( 1 / x )  volt / meter… ( 1 )

As capacitance C = 2πε0εr / Loge ( D / d ) and C = Q / V… ( 2 )
Q = CV

= [ 2πε0εr / Loge ( D / d )] V…. ( 3 )

From equation ( 1 ) and ( 3 )

g = [ V / Loge ( D / d )]  ( 1 / x )

g = V / [ x Loge ( D / d )]  …. ( 4 )

We can say that the potential gradient at any point on cable is inversely proportional to x. The potential gradient is minimum when x is maximum and potential gradient is maximum when x is minimum.

• X is maximum at distance = D ( Internal diameter of sheath ) / 2
• X is minimum at distance = d ( Diameter of conductor ) / 2

### Maximum & Minimum Potential Gradient

• Maximum potential gradient at x = d / 2

gmax = 2V / [ d Loge ( D / d )]   ( ⸫ x = d / 2 )….. ( 5 )

• Minimum potential gradient at x = D / 2

gmin = 2V / [ D Loge ( D / d )]   ( ⸫ x = D / 2 )…. ( 6 )

### Ratio of Maximum to Minimum Potential Gradient

• Therefore, the ratio of maximum potential gradient to the minimum potential gradient

( gmax / gmin ) = {2V / [ d Loge ( D / d )] } / { 2V / [ D Loge ( D / d )] }

( gmax / gmin ) = D / d

• The formula for maximum and minimum potential gradient is applicable only for smooth cylindrical cable.
• The dielectric stress for the stranded conductor increases by 20% due to conductor surface of the individual wires (strands).

You may also like :

Why crushed rock is used at the surface of substation?

Important electricity rules no. 50

Important earthing rules as per IS 1956

Colour code of flexible as well as Non flexible cable