__Total harmonic distortion__- The harmonic distortion is expressed by total harmonic distortion ( THD ).
- It is defined as the ratio of the RMS voltage of all harmonics and RMS voltage of fundamental frequency.
- The THD of the system voltage is given by

THD = √ ( V

_{2}^{2}+ V_{3}^{2}+ V_{5}^{2}+…….. + V_{n}^{2}) / V_{1}
Where

V

_{n}= nth Harmonic voltage in RMS
V

_{1}= Fundamental frequency voltage

__Current harmonic ( THD )__
THD = √ ( I

_{2}^{2}+ I_{3}^{2}+ I_{5}^{2}+…….. + I_{n}^{2}) / I_{1}

__Origin of Current Harmonic__
The origin of
the current harmonic is due to non linear load such as

- UPS
- Television
- Variable Speed drive
- Welding
- Inverter
- Semiconductor circuit

Therefore the
current waveform for such type of load is fundamental frequency and of its
multiple frequency.

__Voltage harmonic__- The voltage harmonic does not produce due to non linear load.
- The current harmonic flows through system impedance and this will result in voltage harmonic drop across impedance.
- This will distort also supply voltage waveform, in this way voltage harmonics are generated.

__Sources of Voltage Harmonic__- Long cable
- High impedance equipment
- High impedance transformer

__Importance of Impedance__- The harmonic voltage distortion in the grid is very low because the grid impedance is very low whereas the source impedance of the DG set is very high therefore the voltage harmonic distortion is very high in spite of small current harmonic.

__Effect of Current Harmonic__- The current harmonic increases the power losses due to RMS current flows through circuit.
- This current affects entire distribution system.
- They may increase hysteresis loss and eddy current loss in the transformer and motor resulting heating also increase.
- This will cause overloading in the neutral conductor, false tripping of circuit breaker, and interference with communication lines.

__Effect of Voltage Harmonics__- The voltage harmonics affects irrespective type of load and affects entire system.
- It affects sensitive equipment as they introduce voltage distortions.

__Voltage harmonics distortion problems__

- Electronics loads : Malfunction
- Motors : Mechanical Fatigue
- Transformers : Increased noise, Possible insulation failure

You may also
like :

## No comments:

## Post a comment