## 07/04/2019

### Design of Lighting System

The design of lighting system depends upon following methods.
1. Watts per square meter method
2. Lumen or Light flux method
3. Point to point or Inverse square law method

### Lumen or light flux method

• This method is useful for uniform illumination in the working plane.
• The illumination in the working plane is calculated by following formula.
Illumination in working plane
= ( number of lamps ) * ( rating of lamps in watt ) * ( lamp efficiency in lumen per watts ) * ( co – efficient of utilization ) / Depreciation factor
OR
Illumination in working plane
= ( number of lamps ) * ( rating of lamps in watt ) * ( lamp efficiency in lumen per watts ) * ( co – efficient of utilization ) * Maintenance factor

### Co – efficient of utilization or Utilization factor

• A light source radiates light in the working plane but working plane does not get 100% light from light source.
• The utilization factor is defined as the ratio of lumen on working area to the output lumen of lamp.
Utilization factor
= lumen on working plane / output lumen of lamp
• As the utilization factor increases, the working plane gets more output from lamp lumen.
The utilization factor depends upon following factors.
• Height of lamp mounting
• Illumination area
• Ceiling and watt colour
• Lighting system : direct, in direct, semi direct
The value of utilization factor always lies less than unity.

### Maintenance factor

• The illumination level of light decreases due to dust on lamp and reflector after some times. This matter is considered in the maintenance factor.
Maintenance factor
= meter candle on working plane / meter candle at starting
= 0.8 when lamp is clean
= 0.6 when there is dust on lamp and reflector

### Depreciation factor

• It is defined as the reciprocal of maintenance factor. It’s value always greater than unity.
• Depreciation factor = 1 / maintenance factor

### Calculation of illumination

N = ( E )( A ) / ( O )( CU )( MF )
Where
• N = number of light fitting
• E = Illumination ( in Lux )
• A = working area ( in meter square )
• O = Illumination of lamp output ( Lumen )
• CU = Co – efficient of Utilization
• MF = Maintenance factor
You may also like :

1. Thanks for sharing this quality information with us. I really enjoyed reading. Will surely going to share this URL with my friends. Succulent Alley

2. Your blog is very valuable which you have shared here about LED light Bulbs I appreciate the efforts which you have put into this blog and also it is a gainful blog for us. Thank you for sharing this here.

3. I generally check this kind of article and I found your article which is related to my interest.christopher wray lights Genuinely it is good and instructive information. Thankful to you for sharing an article like this.

4. Clearly, It is an engaging blog for us which you have provided here about 4 pin led tube This is a great resource to enhance knowledge about it. Thank you.

5. You have made my day by posting such a descriptive post about led lights. I would like to thank you for publishing such a post. Keep Posting. underwater fishing lights

6. believe you possess excellent expertise. outdoor table lamp battery operated

7. The flow of your writing is seamless, making the blog an effortless and enjoyable read. I found myself immersed in your words, eagerly absorbing each sentence. marine electrical wiring supplies